SLT2 12Lpm 14 watt 240v Ultra Violet Light Disinfection Purifier with 40044 ballast controller.
No micro organisms are known to be immune to Ultra Violet light , it’s effective against bacteria, mould, fungal spores, viruses & yeasts. This UV disinfection system represents an economical yet effective solution to water disinfecting without the use of chemicals and has a high flow rate. There is a very real risk of contamination in drinking water from bores, tanks & rivers throughout Australia with even some town supplies carry bacteria & Cysts, Giardia & Cryptosporidium.
This system has a treatment flow rate of 12 Lpm which makes it suitable for single outlet applications where the flow rate is under 12 litres per minute.
It is recommended to have a 5 micron sediment filter before any UV system so the lamp’s protective sleeve does not get covered with sediment build up also by reducing the sediment all bacteria comes in contact with the Ultra Violet light. Water enters from one end and is spiralled around the Stainless Steel vessel for maximum contact time before leaving the outlet port. Depending on your water supply this unit may only need one easy service a year where you remove the lamp protective sleeve and wipe clean for best light output.
Lamps are recommended to be replaced every 12 months to keep the system working at peak bacteria killing performance. The lamp is connected to a ballast which has warning buzzer and indicator lights showing that the system is working correctly. 40044 Ballast.
Lamps are easily replaced by sliding the new lamp inside the quartz sleeve.
The UV vessel is made from 304 Stainless Steel rated at 120psi and has two mounting clips.
These systems are usually mounted vertically but can be mounted horizontally as well.
The UV vessel has 1/4″ bsp inlet & outlet ports.
Dimensions 600mm x 100mm
Maximum killing capacity flow rate of 12 Lpm 240v ballast cord and plug 14 watt 4 pin lamp.
1 Year warranty on S/S chamber and 1 year on ballast, subject to usage. Not suitable for saltwater applications.
It is recommended to use a plug in surge protector before the ballast to reduce the risk of power spikes to the system.
Replacement lamp Part No: UV Lamp 14w 4P F (11018)
Replacement ballast 40044
Replacement Quartz Thimble Part No. 20533
Replacement o-ring seal Part No: 31003